Insulation Piercing Connector Ttd-301f
Apply to the construction distribution system, cable connection low voltage aerial insulating cable connection, low volt3 cable connection, street lamp distribution system etc.
1). Main line: Insulated Cur or Al. Tap line: Insulated Cu or Al.
2). Insulating body is made of high strength, Climatic and mechanically resistant material.
3). Tight bolt is proccssed by corrosion resistance trcated and equipped with tight torque nut so that it can be installed simply, safely and fast, The stable piercing pressure can assure the cable connection up to a pcrfect effection.
4). Watertight connector: Withstanding 6kV flash over in water.
5). Sealed waterproof cap of tap line can prevent water come into tap connection conductor. Waterproof soft cap is for option It can be seperated on right side or left side when it is necessary.
1). Adjust the connector nut tu suitable location;
2). Put the branch wire into the cap sheath fully;
3). Insert the main wire, if there are two lays of insulated lay in the main cable should strip a certain length of the first insulated lay from inserted end;
4). Turn the nut by hand, and fix the connector in suitable location;
5). Screw the nut with sleeve spanner;
6). Screw the nut continually until the top part is cracked and dropped down
|Item No.||Main wire section||Branch wire section||Bolt|